Figure 1. FM-200 Discharge Nozzle
Never attempt to connect union connections with only one wrench. Damage to the
vessel's piping or to the switch's piping could occur. Always use two wrenches.
1. Install the discharge nozzle (figure 1, item 1) on the pipe fitting (figure 1, item 2).
For installation of 180-degree discharge nozzles, ensure that the discharge nozzle's
orifices are oriented away from the adjacent bulkhead.
2. Verify that the discharge holes (figure 1, item 3) are properly aligned.
3. Perform the Follow-On Service procedure at the end of this work package.