4-22. DRY CHEMICAL TANK REPLACEMENT AND REPAIR - continued
Push loose cable (8) end through another new cable sleeve (52). Push cable end back into cable sleeve to
form a loop Just large enough to fit retaining clip (4) through. Secure by crimping sleeve. Repeat for
second cable (8)
Slip one retaining clip (4) into each cable (8) loop.
Install ball valve mounting bracket (7) onto ball valve (9) with two screws (5).
Install ball valve mounting bracket (6) onto ball valve (14) with two screws (5)
(18) Install one retaining clip (4) over ball valve (9) handle m open position and one retaining clip over ball
valve (14) handle m closed position. Install one strip tie (3) between each retaining clip and valve
mounting bracket (6) and (7).
Install fill cap (1) and hand tighten only.
e. Installation (See figure 4-19. )
Remove cap (8) and place tank lifting tool (9) onto tank (10) fill collar. Install cap.
Tank can swing while suspended from a lifting device causing injury to personnel
and/or damage to equipment.
Piping is exposed extending outside of tank and can be damaged when lifting.
Attach lifting device to tank lifting tool (9). Secure tank (10) from swinging and carefully lift. Lower tank
onto unit while aligning mounting holes.
Remove cap (8) and tank lifting tool (9). Install cap and hand tighten only
Install four screws (6), flat washers (7), new lock washers (5), and nuts (4).
Attach rod (2) to valve (3). Install new spring pin (1) Place valve m closed position.
Install cylinders per paragraph 4-11.
Install discharge and charging hose per paragraph 4-15, b
Install lift bar per paragraph 4-21
Fill tank (8) with dry chemical per paragraph 2-10.